04-22-2011 05:35 PM - edited 04-22-2011 05:43 PM
04-24-2011 08:59 PM
As I know, the EMCP3.1does not feature Remote communication function except that you change them into EMCP3.2.
Emcp3.2 use MODBUS RTU with RS485 connection
The EMCPII+ is older panel which use CAT DATA LINK coumuncate with genset.
It needs a protocol translater between EMCPII+ and SCADA(such as PL1000).
The SCADA could build into MODBUS network with top PC as Master and all gensets as Slave.
05-04-2011 02:50 PM
All those gensets have J1939 interface, right?
Do you want to do your own PLC and screen programming, or purchase a complete system?
There are many ways to get J1939 data to MODBUS on RS485 or on TCP/IP, then you can define your own screens and HMI.
Just depends on how much customization you want to do? How "remote" is the control room? 100 meters? 1000 meters? 100KM?
I will write you on your email.